8 Zone, 2 Sound Output Conventional Fire Alarm Control Panel;Fire Alarm System Package Size: 350x280x103mm, 1 set/1 carton. Gross Weight:5Kg.
Conventional Fire Alarm Control Panel with 8 Zones
Key Specifications/Special Features Twelve Style B (Class B) Initiating Device Circuits (IDCs). All zones accept two-wire smoke detectors and any normally-open contact devices. One built-in, Style Y (Class B) Notification Appliance (Signal) Circuits (NACs). Alarm, Trouble and Supervisory, relays standard. 24-volt operation. Resettable four-wire smoke detector power @ 500 mA. Non-resettable power @ 500 mA. One-man walk-test programmable for silent or audible test. Disable/Enable control per IDC. Reverse polarity protection.
The CP1000 Series Conventional Fire Alarm Control Panel is a 24 volt, four to sixteen-zone, Class B, Conventional Fire Alarm Control Panel. Designed exclusively to meet the latest market requirements and future Euro codes, the highly cost-effective CP1000 Series can be used in a variety of low- to mid-sized applications.
Enabling the front panel buttons.
To enable the front panel buttons, the key switch in the top left of the panel
must be turned to the ‘On’ position.
Performing a lamp test.
If the panel is in its normal condition, pressing the Reset button will cause the
panel to perform a lamp test.
Resetting the panel after a fire is detected.
To reset the panel after a fire event, press the Silence button followed by the
Resetting the panel.
If any of the panel functions have been activated, pressing the Reset button
will return the panel to its normal condition.
Silencing/resounding the alarms.
If a fire is detected, the panel will automatically activate the alarm circuits. To
silence the alarms, press the Silence button once. To resound the alarms,
press the Silence button again.
Silencing the internal buzzer.
If a fault is detected by the panel, the internal buzzer will sound. To silence